First clean the surface with emery papers. In case old paint or primer which is not fire rated is applied to the wood, remove it with paint remover or mechanically. Then apply single coat of UGAM F R PRIMER for wood. The primer can be thinned down with pure clean soft water. Primer can be applied with brush or spray. Then after minimum four hours interval apply first coat of UGAMCOAT06022007 with brush, roller or airless spray to the surface. Allow four hours for drying. Then apply second coat of UGAMCOAT06022007 to the surface and again allow four hours for drying. Likewise go on applying the coats of UGAMCOAT06022007 to the surface till you achieve dry film thickness of 700 microns for one hour rating OR 1500 microns for two hours rating. After application of final coat of UGAMCOAT06022007 to the surface allow 24 hours curing. Then apply first coat of UGAM F R TOPCOAT WOOD in desired color shade over UGAMCOAT06022007 for protecting fire retardant coating from weather. Allow it to cure for six hours and apply second coat of UGAM F R TOPCOAT WOOD. This can be applied with roller, brush or spray. The surface will now be ready after 12 hours for regular use. This coating is warranted for five years or first incidence of fire from the date of application. In case surface is exposed to fire, the coating should be re-applied to the surface.
|Anandrishiji Hospital & Medical Research Center
|Steel Strips Wheels Ltd.
|ITC Hotel Hyderabad
|Bharat Forge Ltd
|Elpro Estates Ltd.
|Bengal DCL Housing Development Company Ltd.
|Volkswagen India Ltd.
|Barclays Technology Center
|Goel Ganga Developers
|B P C L and H P C L for all India depots
|Defense land systems India
|O N G C - for offshore and onshore
|New P C N D T buildings
| C-Net Solution
|Kokal Interior Contracts Pvt Ltd
|K P M G Ltd
|Tube Products India Ltd
|Mahindra and Mahindra Ltd
|Aquapharm Chemicals Pvt. Ltd
|ENH Interior Projects – Manikchand Icon
|VerGo Pharma Research Laboratories Pvt. Ltd.
|Innvenue Hospitality Management Pvt Ltd. - Ishanya Mall
|S R Enterprises
|Industrial Electric Services
|York India Ltd, Chakan
|Pressure Vessels (India), Pune
|Quantum Ltd., Mumbai
|Capricorn Plaza Pvt. Ltd., Mumbai
|Shree Sastha Enterprises
|Windsor Realty Pvt. Ltd., Santacruz
|Air Liquide Medical System Pvt. Ltd.
|PMT Machines Ltd, Pune
|Nand-Neel Engineering Services
|Machino Autocomp Ltd., Pune
|Thirumalia Chemicals Ltd., Tamil Nadu
| Naveen Electricals, Karnataka
| Transfix India, Pune
|Rattan Singh Buildtech Pvt. Ltd., New Delhi
|Aim Filtertech Pvt. Ltd. Pune
|Phadnis Infrastructure Ltd., Pune
|Conserve Consultant & Engineers
|M/s Thermal Systems (Hyderabad) Pvt. Ltd.
|Varad Enterprises - Kalyani Global
|ITC Hotel Kolkata
|Shachi Engineering Pvt. Ltd
|Chanda Interiors, Bangalore
|Zelos Developers (P) Ltd.
|Mathew Associates Hook-Up & Weld Services
|Multi Amp Enginners Pvt. Ltd
|Geographics Interiors Pvt. Ltd.
|IAV India Pvt. Ltd.
|Thoughtful Theme Creations Pvt. Ltd
|Accutech Power Solutions Pvt. Ltd
|Alpha Foan Ltd, Pune
|Pinnac Housing Pvt. Ltd., Pune
|Natco Products India Pvt. Ltd.
|Micron Electricals, Bangalore
The technical specification is correct to the best of our knowledge and under test conditions and we do not accept any liability towards misuse and contents of it. Product must be tested for specific use prior to use.